Chimney Height Violations: The 3’:2’:10’ Rule
For Safety purposes, building code requires that a chimney must meet the 3:2:10 requirement. The 3:2:10 requiremnt states that the chimney must terminate at least 3 feet above the highest point of the roof that it penetrates, and be at least 2 feet higher than anything within an imaginary 10’ horizontal radius encompassing the top of the chimney.
This requirement is primarily for two reasons:
1. To ensure nearby combustible objects are less likely to catch fire. Objects such as trees, roofs gables, walls, etc. must all be kept at a respectable distance to prevent an unintentional fire.
2. To keep your fireplace from smoking into your home by trying to ensure the chimney will draft properly. If the top of your chimney is too close to an adjacent object such as a tree, wall, or nearby building, wind may create a high pressure plane that may push air down your chimney and force smoke into your home. In some situations, even though your chimney meets minimum height requirements, it may still need to be extended higher in order to draft properly.
If your chimney is not tall enough to meet minimum building code, A to Z is very experienced at extending chimneys to their proper heights. When it comes to your chimney’s safety and performance, A to Z goes to great “lengths” in ensuring your safety and comfort aren’t “short” changed!
We Accept Credit Cards
Certifications & Associations
Awards & Reviews
A to Z’s Technician did a terrific job cleaning out my dryer vent! He was very pleasant to work with and professional. He cleaned the outside dryer vent ductwork. It hadn't been cleaned in 10 years so there was a lot of lint and buildup in the ductwork. He said there wasn't much airflow going through the ductwork.
That could explain why it was taking so long for the clothes to dry. It was also a huge fire hazard. He cleaned up the area outside. I couldn't even tell he had been there. He pulled off the bottom of the dryer to check for lint build up in the dryer. There was a lot of lint in there too. He said he could clean the inside of the dryer also for an extra charge of $50.00.
I thought that was a very reasonable price so I had him clean the inside of the dryer also. I am very pleased with his work and glad I finally found someone to clean the vent. His company also automatically makes an appointment to come back in tow years to clean it again. The appointment will be in two years for the same date as the original visit. He put a magnet on the front of the dryer with the future appointment date so I don't forget. I will definitely use his service again.
~ Annette Mackin, Granite Bay, CA
Read more »
ServiceCEO Chimney Sweeps Software Business Solutions